Corrosion by “Green Death” in Reboiler Bypass Duct Damper in Power-Generation Plant
At a power plant, C-276 nickel alloy welds (N10276) on a C-276 duct floor completely disappeared in less than half a year. A continuous supply of flue gas came in contact with the closed bypass duct. The unscrubbed combustion products condensed on the cold duct, then the closed damper conducted heat from the chimney and reheated the condensate. Investigation (visual inspection and welded coupon testing) supported the conclusion that the corrosion was caused by “Green Death,” a corrosive medium used to test for pitting resistance (11.9% H2SO4 + 1.3% HCl + 1% FeCl3 + 1% CuCl2) at 103 deg...
Corrosion by “Green Death” in Reboiler Bypass Duct Damper in Power-Generation Plant, ASM Failure Analysis Case Histories: Failure Modes and Mechanisms, ASM International, 2019, https://doi.org/10.31399/asm.fach.modes.c0091330
Download citation file: