When a large LPG low-carbon steel storage tank was put into service for the first time and filled beyond the proof testing level, a brittle fracture crack initiated at a fillet weld between a stiffener ring and the wall. The crack propagated to a length of 5.5 m and arrested. Analysis showed that the plates satisfied the criteria of BS 4741. It was concluded that the cause of crack initiation was the lack of a mouse hole at the junction between the stiffening ring and the wall of the tank. The tank was repaired and put back in service....
M. Lam, Failure of a Steel Liquid Petroleum Gas Storage Tank, ASM Failure Analysis Case Histories: Oil and Gas Production Equipment, ASM International, 2019, https://doi.org/10.31399/asm.fach.petrol.c9001512
Download citation file:
Join ASM International
Being a member of the world’s largest association of materials professionals provides the benefits and resources you need to accomplish your personal and professional goals.