Failure of a Cast Iron Water Pipe due to Graphitic Corrosion
A 25.4 cm (10 in.) diam gray cast iron water main pipe was buried in the soil beneath a concrete slab. The installation was believed to have been completed in the early 20th century. A leak from the pipe resulted in flooding of a warehouse. Once removed, the pipe revealed through-wall perforations and cracking along its axis. The perforations and the crack were at the 6 o'clock position. Investigation (visual inspection, radiography, unetched macrographs, and tensile testing) supported the conclusion that the failure occurred as result of years of exposure to ground water in the soil resulting in graphitic...
Failure of a Cast Iron Water Pipe due to Graphitic Corrosion, ASM Failure Analysis Case Histories: Buildings, Bridges, and Infrastructure, ASM International, 2019, https://doi.org/10.31399/asm.fach.bldgs.c0091384
Download citation file: