Steam Generating and Heat Recovery Equipment
Within the first few months of operation of an 8 km (5 mile) long 455 mm (18 in.) diam high-pressure steam line between a coal-fired electricity-generating plant and a paper mill, several of the Inconel 600 bellows failed. The steam line operated at 6030 kPa (875 psi) and 420 deg C (790 deg F). Metallographic sections, energy-dispersive x-ray spectra, chemical analyses, tensile tests, and Auger microscope analyses showed the failed bellows met the specifications for the material. However, investigation also showed entire oxide thickness was contaminated with relatively large amounts of sodium, calcium, potassium, aluminum, and sulfur, alkali, alkali...