Original carbon steel and subsequent replacement austenitic stainless steel superheater tube U-bend failures occurred in a waste heat boiler. The carbon steel tubes had experienced metal wastage in the form of caustic corrosion gouging, while the stainless steel tubes failed by caustic-induced stress-corrosion cracking. Sodium was detected by EDS in the internal deposits and the base of a gouge in a carbon steel tube and in the internal deposits of the stainless steel tube. The sodium probably formed sodium hydroxide with carryover moisture and caused the gouging, which was further aggravated by the presence of silicon and sulfur (silicates and sulfates). It was recommended that the tubes be replaced with Inconel 600 or 601, as a practical option until the carryover problem could be solved.