A welded joint between lengths of 4 in. OD x 13 SWG copper pipe which formed part of a cold-water main failed by cracking over one-third of the circumference. Microscopic examination of the filler metal showed that it had a structure corresponding to a brass of the 60:40 type commonly used for bronze welding. Failure resulted from dezincification of the joint material from the internal side of the tube. Also, a selective attack on the beta phase had occurred. It was evident that the loss in mechanical strength arising from the corrosion had resulted in the development of cracking...